Gov. of New Brunswick ITT
Tender Revision # 1
610 - Electric Wire
Processed by BIDS on Jan/08/2019
***** AMENDMENT NO. 1
BIDDER QUESTIONS -
Would a Generac SD060 60kw 4.5L be compatible for this?
Unfortunately, the GENERAC SD 060 is powered by a 4.5 Lt and will not meet the 72 hour fuel with 408 gallon of diesel requirement. Therefore, the answer would be no - unless your company can provide documentation that confirms that the unit will operate for this time requirement, and with this amount of fuel.
We cannot meet the March 22, 2019 delivery date.
We assume other manufacturers also won't be able to meet this date.
If a manufacturer cannot meet that deadline, should we submit a quote with our offered delivery date, OR not quote at all?
Vendors shall provide written documentation from the manufacturer which states the expected delivery date of the equipment. The successful vendor would then have twenty-one (21) Calendar Days, after receipt of the equipment from the manufacturer, to complete the work. (ENTER this information in the items added below 1.1 - 3.1)
All other tender information remains the same.
*** SUPPLY, DELIVERY AND INSTALLATION OF GENERATORS ***